Air Conditioning Repairs NOTE: If the Freon is being recovered from the unit, a licensed HVAC contractor must coach outlet purses small be validated to do the job. If the property is rental, all work must be completed by a licensed HVAC contractor. NO EXCEPTIONS. Access: Units must be accessible for inspection, service repair, and replacement without removing permanent construction. A catwalk or passageway must have solid flooring for units located in the attic. Clearances from Combustibles: There should be a minimum of a one inch (1") space between Type B vent pipes and wood or insulation. Installation: HVAC systems must be installed per manufacturer's specifications and the requirements of the currently adopted City of Garland code. Condensate Lines: Condensation from all cooling coils or evaporators must be transported from the drain pan coach outlet coupons express outlet to an approved disposal location. Condensation shall not discharge into a street, alley, coach outlet locations los angeles or other such areas as to cause a nuisance. Insulation of Refrigerant Piping: Piping and fittings for Freon lines must be insulated with 1/2" wall insulation. Gas Appliances: Gas connections must be piped by means of an approved flex connector with an approved listed gas stop. Electrical Requirements: When the unit is located in an attic, a light fixture controlled by a switch must be located coach shoulder bag outlet in the required passageway opening and an electrical outlet shall be provided near the unit.
An electrical disconnect is required for all the equipment. Electric Branch Circuit should be connected to the unit with an approved connector or bushing. Over current protection must comply with the manufacturer's specifications.
Prev: coach outlet purses with changeable covers
Next: coach outlet san marcos